- Three suggested applications for this product: (1) End of branch line restraint for structural attachment. (2) Pitched roof installation. Per NFPA 13 (2002) Sec. 188.8.131.52. (3) May be used as an upper attachment with short hanger rod to omit seismic bracing (per IBC 2006: ASCE 07-05 13.6.8 piping systems).structural attachment to anchor bolt, beam clamp, etc. May be used with a pitched or sloped roof application, to meet requirements of NFPA 13 (2002) Sec 184.108.40.206. May be used as an upper attachment with short hanger rod to omit seismic bracing (per UBC97).
- Underwriters’ Laboratories Listed in the USA (UL) and Canada (cUL) to support up to 4" pipe. Meets requirements of IBC 2006: ASCE 07-05 13.6.8 piping systems. Maximum recommended load for 3/8" ATR is 730 lbs. per MSS-SP58-2002.
- Size Range - 3/8" Rod Attachment